To view our installation videos on YouTube click here
MIDSUN E/FUSING TAPE INSTALLATION VIDEO
Checklist for application:
You will achieve 15kV phase-to-ground insulation when you use one wrap of the tape with a 10% stretch and a 2/3 overlap. 30kV will be achieved with a subsequent wrap.
Keep tape clean – Dust, dirt and moisture on hands or tape will prevent tape from adhering to itself.
Must overlap 100% at the start of the application and continue covering apparatus by stretching tape 10%. Press tape down firmly to ensure that no air pockets can develop.
If there is any possibility to hold water – Allow a place for water to egress out
At the termination of the application – be sure to wrap the tape 100% over itself to avoid flagging.